||Health and Safety Management
||Typically exceeds 100 kPa at 10% compression
|Water Vapour Resistance
||BS EN 12086:1997 / I.S. EN 12086:1998
||> 35 MN·s/g
*This approval is valid for ceiling / soffit installation only, with non-combustible walls. Please contact us for correct installation instructions.
||Spread of Flame Index: 0
Smoke Development ≤ 3
|NCC Group Number
|| AS ISO 9705
Tested in accordance with AS/NZS 5637 as required by NCC
|FM Class No. 4880*
||AS ISO 9705
||≤ 30 m2/S2x1000
|Fire-resistance test of elements of construction
||-/240/240 (HDPE pipe)
** Testing to AS 1530.4 performed in accordance with NCC BCA C3.15 Opening for service penetrations using a 120 mm concrete soffit.
Environmental Data Table
||Non-contaminated insulation site waste is recyclable, but there are currently no facilities in Australia to process returned material
||Re-usable if removed with care (long term of service expected)
||No water used in Kingspan Insulation's manufacturing process
|Blowing Agent Global Warming Potential (GWP)
||Manufactured with a blowing agent that has low GWP
|Blowing Agent Ozone Depletion Potential (ODP)
||Manufactured with a CFC/HCFC-free blowing agent that has zero ODP
||Contains 0% recycled product
Polythene wrap and EPS skids 100% recyclable
The Factory Mutual Approval standard for soffit lining boards is Class Number 4880:2015 (Approval Standard for Class 1 Fire Rating of Building Panels or Interior Finish Materials). Kingspan Kooltherm®
K10 G2 Soffit Board (thicknesses up to, and including, 120 mm) produced at Kingspan Insulation’s Somerton manufacturing facility is certified as achieving Class 1 Fire Rating to Factory Mutual Class Number 4880.
For further details please contact the Kingspan Insulation Technical Service Department or alternatively search for Kingspan Insulation on www.approvalguide.com
This approval is valid for ceiling / soffit insulation only, with non–combustible walls with no height restriction. This approval is valid for any fixing specification. However, for mechanical reasons, the fixing specification and the taping specification must still be followed.